SOLAR SYSTEM INSTALLATION COMPARISON BETWEEN POOR QUALITY AND EXCELENT QUALITY OF SYSTEM INSTALLATION
POOR QUALITY VS RIGHT QUALITY
The installation shows poor direction and panel tilt angle, Due to this the panels do not generate the maximum power to charge the battery bank.
MS structure is used which lasts not more than 3 years
Main wiring has no protection under sun light
Their is no IP65 junction box for interconnection between panels
SOLARAGE always guide and do right installations for our clients by which they can benefit from the system throughout the year.this is the right direction (True South) and tilt angle by which maximum power can be generated for system in 5 hrs a day (according to sun insolation)
GI strut structure is used which has more than 20 years of life.
Main wire is enclosed in conduit pipe upto controller
Interconnection wires are connected in IP65 enclosers
This system is controlled by local make non efficient controller with day night controlling option through relay(fitted in stabalizer box).
their is no DC disconnect switch in the system
Aluminium wires are used in place of copper from array to controller
Solarage always install high efficient controllers with LCD display which shows the battery voltage, Load usage, Grid on/off status, SPV on/off status by which user can understand the functioning of system easily.
DC switch is installed between solar array and controller
System do's and dont's information is displayed for client's benefit
Improper wiring between controller and battery bank
Battery bank of Lead acid batteries
wiring is too thin (6mm sq)for interconnecting batteries
Solarage always do proper and enclosed wiring between controller and battery bank
Battery bank of tubular Exide Batteries
wiring between batteries is done by 16 mm sq copper cable with thimbles
80% of the manufacturers install MS pole with MS powder coated battery box to cut down the cost , which has no life and starts rusting within a year.
Solarage always install GI poles with ABS plastic battery box , which has long life